Business Type: Manufacturer/Factory,Trading Company
Wall Mounted Authentic Easy Use Fast Delivery Addressable Heat Detector
Home, Communication Electronic Products
Instruction manual of H-6002 heat detector
1.Built-in product ID code 2.Using hardware and software filtering to improve the anti-interference ability of the temperature detector 3.2 bus, linkage type,nonpolarity 4.Advanced electronic code technology improves the flexibility of coding 5. Using highly sensitive thermal elements to improve the response speed of temperature sensor.
1.Working voltage: 15-28V Impulse voltage 2.Working current: 1)Standby current: ≤0.5mA 2)Alarm current: ≤3.0mA 3.Type:2 bus(nonpolarity) 4.Encoding: Electronic code 5.Temperature detector's status indication: 1)Normal monitoring status: LED light will blink periodically 2)Fire status: remain lit 3)Failure status: LED light remain off or blink irregularly 6.Operating environment:Temperature-10ºC~50ºC, Relative humidity≤90%RH no condensation 7.Color: white 8.Weight:120g 9. Executive standard:GB 4716-2005
C. Outline diagram
Figure 1:H-6002 Dimensions
1.Installation method Figure 2 shows the installation of the temperature detector
Figure 2 H-6002 installation diagram
86H50 standard embedded box can be used as pre-embedded box; when installation, locate heat detector on the base and rotate clockwise.
2. Wiring requirements: Wire should be RVS-2 * 1.0 mm2 or 1.5 mm2 3. WARNING: Before installing the heat detector, turn off the power and make sure that all the bases are installed securely.
E. Use and operation Encoding operation: you can use our company's hand-held encoder p6010to live coding. When encoding, connect the two clips of the encoder to the two terminals of the linkage, open the handheld encoder power, enter the address code to be written (address code range must be: 1-242, the address code for the same loop is unique). Press the "write code" button, if encoding is successful, the encoder will display the address number after sending the address code. If failed, the encoder will display "FAL" after sending the address code. For details on the steps and methods of encoding, refer to the P6010 Handheld Encoder User's Manual". .
1. The plastic part attached with heat detector is dust cover. Please cover the dust cover after the installation or room decoration, painting construction, so that the smoke detectors are contaminated. 2. The alarm function test of smoke detector should be performed every six months. 3. When the controller detects the cleaning forecast, please send the number of smoke detectors back to the company for cleaning, in order to avoid false or false positives, resulting in unnecessary losses.