1.SIVACON 8PT contains a total of 4 low-voltage switchgear design:circuit design,fixed-mount design,plug in design and pumping design.
2.The current level of bus can be divided into 3200A, 4000A7400A third gear, the cable connection compartment can be In the side or rear, the circuit breaker can be from the connection location, location of test position until the separation of the conversion. Only the circuit breaker in the separation Position is, the door to open, the maximum guarantee of personal security.
3.Fixed-mount enclosure with modular structure, which makes the feed can be any combination of circuits in the cabinet. Fixed or cabinet installation Into the work MCCB, fuse disconnecting switch, or bar-type isolating switch with fuses, and its maximum rated power distribution bus Current is 1400A; bar cabinet power distribution bus fuse protection class IP20B, using 3NJ6 bar fuse switch, the device Replacement of the entire cabinet without having to power down. Power factor compensation and non- counters are choke choke type.
4.Out drawer design with connections for each location, location and separation of test position. 125A drawer above machine with the effort Structure, promoting the process can overcome the friction of the drawer. The maximum rated current of the drawer 630A, drawer modulus is 100,150, 200,300,400,500,600,700 mm.
5.Plug-in design is the fixed device installed in the slab, the slab on the line with the main circuit and auxiliary circuit plug plug Main circuit cable to fixed wiring outlet directly connected to the outlet device. This design is more economical price.