Business Type: Manufacturer/Factory,Trading Company
Slim Surface Ceiling Mount Infrared Sensor Switch (KA-S67)
Corridor, Warehouse, Garage, Toilets etc.
Infrared Sensor Switch
Within 2 Days
Within 25 Days
All Kinds of Lamp
White Box or Customized Color Box
KA-S67 Slim Surface Ceiling Mount Infrared Sensor Switch specification: 1) Power source: 220-240V/AC 2) Power frequency: 50Hz 3) Rated load: 3000W Max. Tungsten 1000W Max. Fluorescent 4) Time setting: (8± 3)S-(6± 0.5)Min (adjustable) 5) Light-control: <10LUX~2000LUX (adjustable) 6) Detection range: 3-8m Max (radii. ) (adjustable) 7) Detection angle: 360° 8) Installation height: 2.5m~3.5m 9) Working temperature: -10~+40° C 10) Detection motion speed: 0.6~1.5m/s 11) Working humidity: <93%RH 12) Standby power: 0.45W(static 0.1W)
KA-S67 Function: 1) Detection field: The detection field is made up of up and down, left and right service field, it can be selected According to the consumer's desire. But the moving orientation has great relationship with the sensitivity. 2) Can identify day and night: The light control can be adjusted freely when it works. It can work in the daytime And at night when it is adjusted on the "sun" position (max); But it can only work in the light control less than 10lux when it is adjusted on the "moon" position (min). As for the adjustment pattern, please refer to the Testing pattern. 3) Time delay can be added continually: When it received the second induction signal after the first it will Compute time once more on the rest of the first time delay basic. (Set time) 4) Light-control potentiometer (LUX): Clockwise the knob to increase its value; Anti-clockwise the knob to Decrease its value. 5) Time potentiometer (TIME): Clockwise the knob to increase its value, the maximum delay time is (6± 0.5) Minutes; Anti-clockwise the knob to decrease its value, the minimum delay time is (8± 3) seconds. 6) Sensitivity potentiometer (SENS): Clockwise the knob to increase its value, the maximum distance is 8m; Anti- clockwise the knob to decrease its value, the minimum distance is 3m.
How To Test KA-S67 Ceiling PIR Sensor: 1) Turn the light-control potentiometer clockwise to Maximal value, the Time delay potentiometer counterclockwise to Minimal value, the Sensitivity potentiometer clockwise to Maximal value. First step: Start the sensor ceiling test under the greater than 1000 LUX Environment (daytime). People walk horizontally in the 8 meters area, Then the sensor will start load to work when it has detected the signal. And Then people stop moving, the load will stop working in 8± 3S. Second Step: Repeat the first step under the the less than 10 LUX Environment (night). The sensor starts to detect.
2) Turn the light-control potentiometer counterclockwise to Minimal Value(night mode), the time delay potentiometer clockwise to Maximal Value, the sensitivity potentiometer counterclockwise to Minimal value.
3) First step: Start the sensor ceiling test under the greater than 1000 LUX environment (daytime). People walk Horizontally in the 3 meters area, then the sensor will not detect. And then people stop moving, the load will Stop working in 8± 3S. Second Step: Start the sensor ceiling test under the less than 10 LUX environment (night). People walk Horizontally in the 3 meters area, then the sensor will start load to work when it has detected the signal. And Then people stop moving, the load will stop working in 6± 0.5Min.