Business Type: Manufacturer/Factory & Trading Company
Rabbit ACSR Congductor of CCC
ISO, CCC, VDE
Aluminum Conductor Steel Reinforced
DC & AC
High Voltage Cable
Construction, Overhead, Power Station
Standard Export Wooden Drums
BS, DIN, ANSI, IEC and so on
All Aluminum Conductor(AAC)& Aluminum Conductor Steel Reinforced(ACSR))for ASTM (AAC, ACCR, AAAC, ACSR) Generally Confirming to IS 398 (Part-I, II, IV), IEC-228 (AAAC) Conductor as per ASTM-B-399-1992 (AAAC) Conductor as per BS-3242-1970 (AAAC) Conductor IS: 398-IV-1994 (ACSR) as per ASTM-B-233-1992 (AAC) as per BS-215-1-1970 (AAC) as per IS-398-1: 1976 (AAC) as per ASTM-B-231-1990 (ACSR) as per IS: 398-II: 1976 & IS: 398-V: 1992 (ACSR) BS-215-II-1970 (AACSR) as per IEC-1089-1191 AAC(All aluminum conductor) are suited for overhead power line. We can supply this conductor according to different recognized standards, such as IEC61089, BS215, BS EN 50182: 2001, STM B231, CSA C49, DIN480201, JIS C3109, customer special specification also can be satisfied. ACSR or ACSR cable or ACSR conductor used for Overhead electrical distribution and transmission lines for distributing power Applications Used as bare overhead transmission cable and as primary and secondary distribution cable. ACSR offers optimal strength for line design. Variable steel core stranding enables desired strength to be achieved without sacrificing ampacity.
Construction Aluminum alloy 1350-H-19 wires, concentrically stranded about a steel core. Core wire for ACSR is available with class A, B, or C galvanizing; ""aluminized"" aluminum coated (AZ); Or aluminum-clad (AW). Additional corrosion protection is available through the application of grease to the corer or infusion of the complete cable with grease.
Specifications ACSR bare conductor meets or exceeds the following ASTM specifications:
Notes Resistance is calculated using ASTM standard increments of stranding and metal conductivity of 61.2% IACS for EC (1350) and 8% IACS for steel. AC (60Hz) resistance includes current dependent hysteresis loss factor for 1 and 3 layer constructions. Current ratings are based on 75oC conductor temperature, 25oC ambient, 2ft/s wind, 96/watts/sq. Ft sun, 0.5 coefficients of emissivity and absorption.