Business Type: Manufacturer/Factory & Trading Company
Wuhan, Hubei, China
The machine GDZL-100L can effectively remove moisture, gas and impurities in the insulating oil, improve the pressure resistance of the oil and the quality of the oil, to ensure the safe operation of the power equipment. It is mainly used in the power sector and industrial and mining enterprises to deal with unqualified transformer oil, transformer oil, switch oil and so on.
1. Small size and high efficiency, easy to move. It is especially suitable for live working on site. It also can dry the moisture of power equipment, and conveniently vacuum the power equipment.
2. Infrared liquid level automatic control device, system pressure automatic protection device and high-efficiency degassing components are adopted in the structure. The operation is convenient and safe.
3. The phase sequence protector is installed to protect the equipment motor from phase loss and low voltage operation. Make the device more secure.
1. Capacity: 100L/min.
2. Working temperature: 0ºC~45ºC.
3. The altitude of the site will directly affect the vacuum of the machine. The higher the altitude, the lower the vacuum (negative value).
4. The oil to be treated should not be too dirty (that is, there are too many impurity particles in the oil), otherwise, it must be fully filtered with other filtering equipment to avoid affecting the degassing efficiency of the oil machine or blocking the filter elements and affecting the life of the oil machine.
5. When the vacuum pump is working, pay attention to the oil condition indicated by the oil mark (the oil should be on the oil mark line). When the water is much in the vacuum pump oil, the oil should be replaced in time.
6. When operation, if there is more water in the cooler, it should be released in time.
7. Always pay attention to the change of pressure gauge value. When the pressure is >0.3Mpa, the filter should be cleaned or the filter element replaced.
8. The filter screen of the primary filter, the secondary filter and the fine filter should be removed and cleaned frequently, and kept clean to avoid blockage, that resulting in insufficient oil or excessive pressure.
9. During operation, pay attention to whether the running noise of the pump and the corresponding motor is normal. If abnormal, it should be eliminated immediately.
10. When the machine is not in use, the residual oil in the oil machine should be put out for use.
|1||Vacuum System||Vacuum Pump||Domestic||1set||Pumping vacuum|
|Vacuum Pump Motor||Original Parts||1set||Start vacuum pump|
|2||Oil Transfer System||Oil Pump||Joint Venture pump||1set||Pumping oil|
|Oil Pump Motor||Original Parts||1set||Start oil pump|
|3||Three-dimensional Vacuum Dehydration and Degassing System||Three-dimensional Flash Evaporator||Using DG-SWLT Technology||1set||Super dehydration and degassing capacity|
|Thin Film Molecular Evaporation|
|Microgram System||HV HIPOT||1set|
|Vacuum Separator||HV HIPOT||1set|
|4||Filtration System||Primary Filter (Stainless Steel)||HV HIPOT||1set||Filter out impurities above 80μm|
|Secondary Filter||Polymer Materials||1set||Filter out impurities above 50μm|
|Fine Filter||Polymer Materials||1set||Filter out impurities above 3μm|
|5||Vacuum Display System||Vacuum Meter||Famous Brand||1piece||Display vacuum degree|
|6||Level Regulating System||Infrared Liquid Level Controller||HV HIPOT||1set||Normal operation of constant oil filter|
|Automatic Level Controller||Solenoid Valve Factory||1set||Automatic control of oil intake and output|
|Manual Level Controller||BOPU||1set||Manual control of oil intake and output|
|7||Heating Control System||Heater||BANK||1set||Increase oil temperature and reduce oil viscosity|
|Temperature Controller||Shanghai Yichuan||1set||Automatic constant temperature|
|8||Pressure Control System||Pressure Gauge||Hongqi Group||1piece||Display pressure value|
|Pressure Controller||Joint Venture Brand||1set||Protect the filter element from damage|
|Condenser and Cooler||HV HIPOT||1set||Condensation into liquid water|
|Water Tank||HV HIPOT||1set||Water storage, water release|
|9||Electrical Control System||Electrical Control Cabinet||HV HIPOT||1set||Controlling the normal operation of oil filter|
|Trinity Protector||HV HIPOT||1set|
|10||Accessories (Pipes and Tanks)||Domestic||1set||Oil circulation|