It is used to inject ultralow frequency pulsating DC signal to the fault line.
The transmitter panel as below:
Power socket: contact with 220V power
Protective tube: change protective tube if needed
Power switch: turn on/off the device
HV on: when turn on the device, press this button when output adjustment on the ZERO position to output HV signal.
HV off: Stop HV output
Zero: indicate that the output voltage on the zero position
Protect: when the device become protect mode, this indicator will be bright to show the device is in protect blocking state. Adjust the Output adjust button to Zero position to reset the indicator.
Output adjust: adjust the output current and voltage. When it on the Zero position, to press HV on button to start the transmitter signal output function.
Protect current: indicate the input current value. If current is over default max. 4A,the device will be stopped. Then it is needed to zero the output adjustment button to set protective circuit to readjustment the current.
Output voltage: indicate the value of output voltage
Earth: earth terminal to contact with the earth line to connect the earth mat.
HV out: connect the fault line. According the local state to clip the switchgear wire or connect the faulty line with rod of patch board
Test ground: connect with earth mat.
3. Method of application
3.1 Work principle
Transmitter output is impulse DC signal which frequency is 1Hz.Low frequency less impact by the system division capacitance. It is proved the 1Hz signal can satisfy most requirements from the testing site.
The limited voltage of the transmitter is 8kV.It is equal the phase voltage peak value of 10kV line. If the voltage too high, it will bring line major insulation broken. If it's too low, the fault can't be reappeared. This value could be adjusted when production.
Hanging the sensor along with the line to test the current. Sensor test the current on the line and automatic zero setting then converse analog signal into the digital signals to transmit by wireless mode.
3.2 Operation of the transmitter
First beak the fault line, then connect the it with utility power(220V).Connect the earth line with Protect ground terminal and the earth grid.
Wire the earth test line (HV line with black clip) to the earth test grounding and earth gird.
We could wire the output line of the fault line according the site conditions. Connect the short line which has a red clip with the line terminal and the line side of the switchgear. If must connect it on the overhead line ,we suggest to use the long line. Connect its high voltage outlet with the line terminal, and then connect the other line on the insulation hanging rod, then hang the rod on the fault line.
3.2.2 Power supply
Open the power switch. Now the transmitter still doesn't transmit.
3.2.3 Start and output
First adjust the output adjust button to ZERO.Now the Zero is bright.
Then press HV on button to begin the output. Now the HV indicator is light.
Turn up the output adjust button slowly to rise the current but make sure the protective indicator doesn't light. If this indicator light, it indicates the faulty line has small resistance so the input current is too high. Now it's needed to adjust the output adjust button to ZERO anticlockwise and readjust to suitable position.
3.2.4 Stop output.
If need to stop the output, press HV off button
3.2.5 After test, turn off power and disconnect the wiring.
We have passed ISO9001:2015,CE,SGS approval and IEC report
Tianjin Grewin is concentrating on transformers for 20 Years and complianted by ISO9001:2015,CB,IEC CB,CE etc.We're always pay great attention to its business philosophy "Quality and Honesty First".Grewin is specialized in the design and manufacture of wound components such as transformer,current sensors, chokes etc .windely used in communications,electronics,meters,industrial control,medical equipments and other fields.We are also a provider of power meters and instruments locators. 85% of its products exported to America, Europe, and Asia etc.We sincerely invite you to join us to create a bright future.
3.Terms of Shipment:
Within 10 working days after received related prepayment or L/C.
(1)T/T 100% or 50% deposit by T/T in advance, balance amount to be paid 7 days before
(2) By irrevocable L/C at sight, to be issued immediately against confirmed order.
(3)Payment by T/T, if order amount is less than USD 20,000.
(1)We provide 1 year warranty.
(2)If the product is defective, please notify us within 3 days of delivery.
(3)All products must be returned on their original condition, in order to qualify for a refund or exchange of goods
6.Why choose us?
Quality and honest first!
A. Flexible service for diffierent transformers with high efficiency performance.
B. Over 40 years experience of transformer designing and producing.
C.100% test of every single product we produce from incoming material checking.
D. UL, CE, ISO9001:2008
E. We offer custom-made transformers, OEM and ODM are welcome
F. We deliver the quality you expect at consistently competitive prices
G.Transformer quality lifetime:10 Years.
H.Specialty Sales service:5 -10 Years
7.Flow chart of trading activities:
Request for quotation
Offer and counter offer
Sending and receiving samples
Placing a firm order
Paying and receiving the down payment
Factory production & Quality inspection
Paying and receiving the balance
Delivery of goods
Tianjin Grewin Technology Co.,Ltd.
Address: 2# MeiNian Plaza No.16 DongTing Road,Hexi Distr,300222,Tianjin China.