Fully Auto Pure Water Treatment System/Drinking Water Treatment Filter/Reverse Osmosis For Mineral Water
RO Mineral Pure Drinking Water Purification Purifying Treatment System Equipment Machine Plant
Water treatment machine, the raw water is tap water, first goes by pre-treatment, then by RO treatment. Through those treatments, can remove dissolving salt 99% and harmful materials, like particle, colloid, organic impurities, heavy metal ions, bacteria, viruses and heat source, etc. The system salt rejection rate gets 96-98%, output water conductivity gets ≤ 10μ S/cm² .
Function of the machine:
RO membranes auto wash and manual wash
RO membranes manual wash wite medicine
Pure water high water level auto stop, low water level auto start
Multi-phases pump protected without water
Protected when no power, poor power, larger electrical current
Short circuit, creepage of electricity
The system process
Raw water raw water tank raw water booster pumpmechanical filteractivated carbon filter (water softener machine)precise filter (cleaning device) high-pressure pumpReverse Osmosis Componentspure water tank(Ozone device/UV device) pure water.
The system description
1. Quartz sand filter
Raw water into the filter for a simple mechanical filter, mainly to remove suspended solids in water, colloidal particles and other large impurities in the water when the water pressure and the pressure difference over 10Psi (0.7kg/cm2) or water SDI> 5, the need for backwashing. In general, before running back wash once a day.
2. Activated carbon filter
Activated carbon is used wood, coal, shell (nuclear) and other carbonaceous material through chemical or physical method activation made. It has a very large number of pores and specific surface area, which has a strong physical adsorption capacity, the effective adsorption of organic pollutants in water. Primarily to remove organic matter in raw water, chlorine, odor, color, etc., so that the original residual chlorine in water ≤ 0.1mg / l, effective protection of RO membrane from chlorine damage to parts of activated carbon typically 12 to 18 months to replace a The main residual chlorine as determined in raw water.
Under normal circumstances, it needs to backwash once a week.
3. Precise filter
The third pretreatment, filter spray for the polypropylene melt, filter housing is ABS material, mainly to remove the vast majority of very fine suspended solids.
RO water purification system/machine/equipment
After-sales Service Provided:
The machine which we supply to you, we can give you one year after-sale warranty,
We also can arrange our engineer(s) to your factory to install the equipment and train your staffs by your requirment, but you should pay the round air ticket cost and arrange the hotel accommodation for our engineer(s).
|Model||Capacity (M3/H)||Power (kw)||Recovery Rate (%)|
Total land area
LX W X H (mm)