Packaging Details: 200 pieces of pendent fire sprinkler nozzle, fire sprinkler system is generally packed in one carton, with plastic box inside for further protection during transportatin Delivery Detail: Within 7 working days for 5000 pieces of fire sprinkler nozzle Specifications
68 degree fire protecton sprinkler 1. Differtent style for your reference and choice; 2. Heavy weight; 3. ISO, SGS
68 degree fire protecton sprinkler
DEACRIPTION Each closed-head sprinkler is held closed by either a heat-sensitive glass bulb (see below) or a two-part metal link held together withfusible alloy such as Wood's metal and other alloys with similar compositions. The glass bulb or link applies pressure to a pipe cap which acts as a plug which prevents water from flowing until the ambient temperature around the sprinkler reaches the design activation temperature of the individual sprinkler. Because each sprinkler activates independently when the predetermined heat level is reached, the number of sprinklers that operate is limited to only those near the fire, thereby maximizing the available water pressure over the point of fire origin. The bulb breaks as a result of the thermal expansion of the liquid inside the bulb. The time it takes before a bulb breaks is dependent on the temperature. Below the design temperature, it does not break, and above the design temperature, it takes less time for higher temperatures. The response time is expressed as a response time index (RTI), which typically has values between 35 and 250 m½ S½ , where a low value indicates a fast response. Under standard testing procedures (135 ° C air at a velocity of 2.5 m/s), a 68 ° C sprinkler bulb will break within 7 to 33 seconds, depending on the RTI.  The RTI can also be specified in imperial units, where 1 ft½ S½ Is equivalent to 0.55 m½ S½ . The sensitivity of a sprinkler can be negatively affected if the thermal element has been painted.