Hangzhou, Zhejiang, China
Member Since: 2011
Business Type: Manufacturer/Factory & Trading Company
1.About Lightning Arrester
0.25~500 KV Product's Characteristics:
1.The Core column applied winding structure, Polymer Housed core pillar molded on the core column,
with almost no internal air gap, and outstanding sealing performance Simple in structure, small in size
and light in weight
2.Polymer Housed with flexible silicone rubber, explosion-proof ZnO varistor as the core component
is large in flow capacity which is much higher than that of the
3. national standard GB11032 and ANSI 62.22, and with high reliability. With fully insulated tops, the
product can be applied to the complete cabinet installation, which can reduce the designing size of cabinet.
4.Products with detachment device can provide signals for quitting operation when failure occurs,
avoiding arrester explosion, and it is maintenance-free.
5.Polymer housed products with a six CTI level,creepage distance meets the requirements of IV level in
heavy pollution areas.
2.Lightning Arrester detail picture
3. Lightning Arrester Working Condition
4. Lightning Arrester detail shipping information
5. Lightning Arrester Other information
Our company is founded in 1993year, with advanced technology and talents. To provide customers with the
most satisfactory product quality and thoughtful service. We hope to develop together with you hand in
hand,and make both of us win-win. I hope the majority of buyers can come visit and tour company,
your satisfaction is our greatest pursuit.
Production Lead Time & Quality Guarantee:
sample deliery time is about 2-3days
big order quantity is about 30-35 days after we receive 30%~50% deposit from you.
Generally,it takes 4 working days by DHL/UPS ,and 7-10days by EMS
12months' warranty period. 20years' quality guarantee period
Our salesmen will reply your inquiry within 24 hours. Any order is welcome. If you like to be our agent in your
country, we can give you any support on the technique & other aspects.
|Rated voltage---------kV||30||4/10µS High current impulse kA||100|
|MOCV ----------------kV||24.4||Lightning impulse withstand kV||200|
|Nominal Current-------kV||10||Power frequency voltage withstand(dry/wet)kV||70|
|Residual voltage of steep impulse----at 5kA(kV)||88.5||0.1S TOV--------------kV||36|
|8/20µS Residual voltage of lightning impulse current kV(Peak value)-----at 5kA(kV)||81.6||1S TOV----------------kV||34.5|
|Residual voltage of switching impulse current kV (peak value)----at 1kA (kV)||62.5||10S TOV---------------kV||33|
|1mA D.C reference voltage (kV)||42.5||1200S TOV-------------kV||30|
|Line discharge level||1||Creepage distance ----mm||1082|
|2mS long duration impulse current A||400||Material employed in series non-linear resistor||Zinc Oxide|